9.2.4. Table of terminal units<br>

### 9.2.4. Table of terminal units

The “terminal units” table displays results for all terminal units in the system assigned to particular sources. The type and name of the source is displayed at the top. This is followed by results for ungrouped components, then by results for components of groups.

TU symbol. | symbol (name) of terminal unit |
Room symbol | symbol (name) of room with the terminal unit |
ti/qi | temperature inside the room | [0C]
Q/Fspec | specified output of terminal unit | [W]
Q/Fsize | sized output of terminal unit | [W]
Q/Fgains | heat gains from pipe-runs and circuit pipes | [W]
G | flow rate | [kg/h]
ts/qs | supply temperature | [0C]
tr/qr | return temperature | [0C]
Radiator type | sized or specified radiator type |
L | sized or specified radiator length | [mm]
H | sized or specified radiator width | [mm]
D | sized or specified radiator width thickness | [mm]
SPR | number of connection pipe-run – supply |
RPR | number of connection pipe-run – return |
Press. drop | pressure drop across terminal unit | [kPa]
A’/A | oversizing or undersizing of terminal unit (percentage) | [%]

When the project includes integrated radiators, table of results for fittings assigned to these terminal units is displayed under the table of results for terminal units.

TU symbol. | symbol (name) of terminal unit |
Room symbol | symbol (name) of room with the terminal unit |
Valve name | type of valve (catalogue name) |
Diam. | valve diameter | [mm]
Press. drop | pressure drop on control component | [Pa]
Xp | value of proportional control deviation (for some valve types) |
Va | valve authority |
Setting | sized setting or plate orifice |